Routine check on DGS maintenance day (1/7)
Check if the power supply can be controlled by BIO.
Check if the script can be started.
Confirmed that the limit switch installed is in Green.
The following settings were made.
Set the software limit of ETMX and ITMX GAS.
Enable the HW limit switch of SRM.
Confirmed that the Release Sensor is 0. 1: Seated
ETMX, ETMY, ITMX, ITMY : No problem
Ping Test is performed.
ETMY (rebooted on 2022/1/6)
=> Confirmation only, no recovery work was done.
PCAL(EX1,EX2,EY1,EY2):Not confirmed because it is ON only when used.
Check if the temperature acquisition is working properly.
Precision air conditioning
Is the temperature acquisition function working properly?