Routine check for DGS maintenance day (1/21)
Check if the power supply can be controlled by BIO.
Check if the script can be started.
Confirmed that the limit switch installed is in Green.
The following settings were made.
Change the value of software limit of ETMX and ITMX GAS (E2213706-v3)
The HW limit switches on the ETMX IP were all red because the cable had been unplugged during the leak test, but later checks showed that they were all green, so no problem.
Confirmed that the Release Sensor is 0. 1: Seated
ETMX, ETMY, ITMX, ITMY : No problem
Ping Test is performed.
=> Confirmation only, no recovery work was done.
PCAL(EX1,EX2,EY1,EY2):Not confirmed because it is ON only when used.
Check if the temperature acquisition is working properly.
Precision air processer
Is the temperature acquisition function working properly?